On-line Partial Discharge FAQ
皇冠足彩Have some questions about Partial Discharge? Why not check the frequently asked questions (FAQ) below? You might find answers to most of your questions.
If you cannot find answers to your questions, please do not hesitate to email us firstname.lastname@example.org
IPEC PD Monitoring Systems
Q1. What PD monitoring systems do IPEC offer?
Q2. Can on-line PD monitoring be used on transformer HV bushing?Yes, HV bushing monitoring is possible where the bushing has a bushing tap. In this case, a simple adaptor is used to connect directly to the PD Monitoring system. Normally each bushing would be monitored separately.
Q3. How often should on-line PD monitoring systems be inspected or calibrated when they are in service?
皇冠足彩We normally recommend a full health check which includes calibration every 24 months.
The monitors have built-in system diagnostics that continually check the PD monitor health and raise an alarm if maintenance is required.
Q4. Can end-user perform reliability analysis with the system? Is it possible to export data?
The PD data can be analysed in detail using the many graphing tools on the iSM website.
皇冠足彩Data can also be exported in .csv format if required
Q5. How can IPEC’s PD monitoring system pick out PD in a high noise level environment
IPEC use our DeCIFer™ Algorithm which we designed to distinguish between PD and noise. Our ASM皇冠足彩 samples signals at 100MSample/sec and 14-bit resolution, which means we will be able to have high-resolution data and be able to see small PD spikes even among large noise. Our DeCIFer™ Algorithm uses Wavelet Analysis to effectively picking out potential PD signals from noise, and then uses PD Knowledge Rules Analysis which is based on IPEC’s experience of over 20 years of PD data analysis. These enable our DeCIFer™ Algorithm to effectively differentiate PD from noise.
Q6. Can IPEC’s PD monitoring system detect cable PD if there are lots of joints on the cable?
One HFCT on one side of the cable can normally monitor upto 4-5 km of cables (with cable joints in between). If cables are longer, we recommend installing HFCT and monitoring systems at both cable end. Or, if cable earth is accessible at each cable joint (at link box), we can install HFCT and ASM at cable joints for full coverage of cable PD monitoring.皇冠足彩 This is a common application in EHV networks.